Furnace Repair in Redford, Michigan
Is your heating system not working, or perhaps behaving a little differently? Have you noticed that your home in Redford, MI is not maintaining temperature properly and making funny noises?
If your gas furnace is not working call Advanced Heating and Cooling now. We fix broken heating equipment all the time in Redford, MI. Or if your system is just getting old, or giving you reasons not to trust it any more let us know. We have many years of experience and we can help you make the right choices when it comes to your furnace system.
Performed safety inspection on Forced Air Heating System. Found 0 PPM CO at this time. All safety controls operating correctly at this time. Lennox. MODEL #: 61404-80-6. SERIAL #: 5884L0 7677.
repaired pressure switch was stuck
Inspected furnace found faulty wiring and bad connection. Replaced terminals and wiring with new wire nuts. Issue resolved.
Inspected forced air heating unit. found bad ignitor. Replaced. Unit is working now. Found 0 ppm co at this time. All safety controls operating at this time.
Furnace short cycling by high limit. Heat exchanger looks okay, a/c coil clogged. Switched high speed on blower to see operation. working.
Checked furnace found low gas pressure from valve causing yellow flame. Sooting and intermittent operation.. Maxed out pressure setting on gas valve to compensate. Due for replacement. . Went out the next day and replaced with refurbished gas valve . Cleaned soot from burner, cleaned flame sensor, cleaned inducer & checked condo pump and humidifier.
Inspected forced air heating unit. Found 0 ppm co at this time. All safety controls operating at this time. Chimney clean but fireplace needs normal maintenance for use.
Inspected forced air heating unit. Found 0 ppm co at this time. All safety controls operating at this time.
Looked at forced air heating unit. Found 0 ppm co at this time. No faults in safety controls at this time.
Inspected forced air heating unit. Found 0 ppm co at this time. All safety controls working at this time.