Furnace Service and Repair Redford, Michigan
If your gas furnace in Redford, MI is not working it is likely your furnace needs repair or service. At times the fix is simple, other times it is not. Our heating and furnace service technicians have years of experience working on furnaces like yours in Redford, MI. Advanced Heating and Cooling has service vehicles on call that are fully equipped with the tools and parts necessary to get your furnace back up and operating.
Our furnace repair, furnace service or replacement pricing is very competitive. Our estimates are always firm with no hidden surprises. You can rely on Advanced Heating and Cooling to advise you properly and to do excellent work promptly. Ask us about maintenance agreements for your high efficiency furnace today.
We provide gas furnace service in Redford, MI
We provide gas furnace repair in Redford, MI
Performed safety inspection on Forced Air Heating System. Found 0 PPM CO at this time. All safety controls operating correctly at this time. Lennox. MODEL #: 61404-80-6. SERIAL #: 5884L0 7677.
repaired pressure switch was stuck
Inspected forced air heating unit. Found 0 ppm co at this time. All safety controls operating at this time.
Checked furnace found low gas pressure from valve causing yellow flame. Sooting and intermittent operation.. Maxed out pressure setting on gas valve to compensate. Due for replacement. . Went out the next day and replaced with refurbished gas valve . Cleaned soot from burner, cleaned flame sensor, cleaned inducer & checked condo pump and humidifier.
Furnace short cycling by high limit. Heat exchanger looks okay, a/c coil clogged. Switched high speed on blower to see operation. working.
Inspected furnace found faulty wiring and bad connection. Replaced terminals and wiring with new wire nuts. Issue resolved.
Looked at forced air heating unit. Found 0 ppm co at this time. No faults in safety controls at this time.
Inspected forced air heating unit. Found 0 ppm co at this time. All safety controls working at this time.
Inspected forced air heating unit. found bad ignitor. Replaced. Unit is working now. Found 0 ppm co at this time. All safety controls operating at this time.
Inspected forced air heating unit. Found 0 ppm co at this time. All safety controls operating at this time. Chimney clean but fireplace needs normal maintenance for use.
Inspected forced air heating unit. Found 0 ppm at this time. All safety controls operating at this time. Suggest rinsing the reusable air cleaner for more air flow.